pe water pipe in roll,
used for water supply,
made by HDPE, PE-100
work pressure: 16PN, 16bar
OD: 20mm or 1/2', 1500m/roll
pe water pipe in roll,PE water pipe in roll,
Applies to the piping system of drinking water supply, irrigation, spray garden pe duct etc. Color: Black is the base color, color code on the surface of the duct is distinguished by brown, grey, orange, blue, red, purple, green and yellow. Product supplying is based on requirements.
1.The internal wall of the duct is so smooth that cable blowing technology can be selected for optical cable and cable laying, which makes the construction simple, quick and economic.
2. Moisture resistance, corrosion resistance and long service life.
3. Good insulating performance and long service life (underground duct can be used for 50 years), durable, easy for maintenance, ensure of a safe operation of the line.
4. The duct can be coiled with not much joints, easy for installation, and duct length can be as long as 3000m. High pressure resistance, system enlarging, maintenance is very convenient and cost is low.
Dimension (unit: mm):
inside and outside walls should be smooth, homogeneous, no potholes formed by defects and impurities; appearance of uniform color, no color lines and spots decomposition; section without air bubbles, cracks; closely fused silica core wall, no excuse phenomenon; external wall of products identify complete and clear.
2. ring-stiffness. KN/m2
Vertical pressure distoration rate is 40% of original diameter, immediate unloading, the specimen is not broken, not hierarchical
Vertical pressure distoration rate is 30% of original diameter, immediate unloading, the specimen is not broken, not non-layered, outer diameter would naturally be restored to its original 90%.
6.elongation at break,%
7.max tractive load,N
8.falling weight impact test
Temperature 0 , height 2m, with the impact of 2Kg heavy hammer 10 times, nine times or more shall be no cracking phenomenon
10. hydraulic pressure leadagetest
Temperature 20 , the pressure 50Kpa, maintain 24-hour, the sample connector, pipe plugs no leakage.
11. portrait retraction rate,%
12.cold bend radius,mm
13. internal wall friction coefficient
Static (plate method)
Dynamic (Drum Method)
14. power frequency break down,KV/mm
The sample were placed in 5% NaCL, 40% H2SO4, 40% NaOH solution soak for 24 hours was no obvious corrosion.
Note: Other sizes and shape are also available upon request
Remarks: The pipe products are agree with National or Industrial Standards and Certifications.